The DS line of air circuit breakers has been a tried and tested product line of low voltage air circuit breakers that have been proven to be both versatile and reliable for decades. Originally, it was sold as a Westinghouse product, then the line was later sold to Square D and then Eaton Cutler Hammer. It is widely understood that all of these breakers are interchangeable regardless of label, however the same does not hold true when replacing the switchgear parts. The switchgear cabinets have been manufactured in several locations around the country which resulted in six different lines of cabinets. Care must be taken to properly identify which style of cabinet is in question to properly identify and acquire interchangeable parts.
The first vintage of DS switchgear was manufactured by Westinghouse in East Pittsburgh in 1969 and continued through 1973. It can be identified as having “Shop Order” (SO) numbers that start with “24Y”. The second vintage also made in East Pittsburgh through 1984 with SO numbers that started in “27Y” and concurrently with “WPA” switchgear made in St. Louis and was designated by a “General Order” (GO) number rather than a shop order number. The East Pittsburgh gear was generally marketed to heavy industrial users and the WPA gear for commercial applications.
Two more vintages came out of the St. Louis plant, designated as vintage III and IV. Vintage III was an attempt to merge the “27Y” product line with the WPA product line and it is usually designated with a prefix of “28Y”. It was a very short production run during 1984 from May through October. Vintage IV was made in St. Louis form October 1984 through May of 1990 - it continued to use the GO number system and also the “28Y” SO numbers. In 1990, production was moved to Asheville, NC and although changes had been made to the design, the “28Y” SO number system was continued.
Finding Replacement Parts for DS Switchgears
If this sounds confusing, you have a lot of company. So how does someone go about finding replacement parts to maintain their DS switchgear? If you are fortunate enough to have the original product literature (see below) it will help to some degree. However, because much of it is no longer manufactured (new) you will more than likely find yourself relying on a reputable used electrical equipment dealer like NPE. If you know the SO number, GO number and production dates it will help narrow the focus, but even within product lines things like bus size and length will change depending on the configuration and rating of the switchgear.
Cutler Hammer DS and DSL Low Voltage Power Circuit Breaker Renewal Parts - Manual RP.22B.01.T.E.
Westinghouse Instructions for Low Voltage Power Circuit Breakers Types DS and DSL – Manual IB 33.-7901G
Instructions for Type DS Metal-Enclosed Low Voltage Power Circuit Breaker Switchgear Assemblies – Manual IB 32-690-E
The fastest and most reliable way to get the right part, at the right price, at the right time will be with photos and measurements using the NPE "On the Go" with your smartphone. NPE "On the Go" is very easy to use, just open it up and navigate to Switchgear/Switchgear Parts, answer the product driven questions and attach photos that you’ve taken with your mobile device. This RFQ will be sent to the NPE technical staff where it will receive TOP PRIORITY! Of course, you can still contact us with your requests and questions.
NPE "On the Go"